Rated at 4-stars, the Hotel ILUNION Pio XII in Madrid, Spain sought to save energy in their kitchens. In 2014, they hired Melink to install Intelli-Hood® demand control kitchen ventilation as a means to reach this goal. Here is more information regarding the hotel kitchens:
- Total motor power: 6 HP
- Daily operating hours: 14
- Days per week: 7
- Weeks per year: 52
- Cost per kilowatt hour: 0.11 EURO
Intelli-Hood saved 8,072 EURO in utility costs and reported an average fan speed of 56%. This resulted in a 2.1 year payback and and reduced carbon emissions.
Below is a sample graph of the varying exhaust fan speed for one day at the hotel:
And the below graphic indicates the before (navy) and after (green) reductions in kilowatt hours, heat load, and exhaust volume:
Could Intelli-Hood be a fit for my project?
Are you curious how much energy Intelli-Hood could save within your commercial or industrial kitchens? Submit an energy savings estimate request form at the bottom of our Intelli-Hood page to get started.